The KazElectroSnab plant manufactures package transformer substations with a rated power of 180 to 560 kVA with the following versions: , CTS-560-T. At the same time, substations with a capacity of 180 kva are only single-transformer, the rest are both single and double transformer. two-transformer substations are equipped with two single-transformer substations, between which there is a cabinet with a sectional machine. For substation 560 kVA, the cabinet is equipped with an ATS device. For reasons of better operating conditions and reduction in the length of the switchgear, two-transformer substations can be installed in two rows. For this purpose, the plant supplies a special bus duct connecting the busbars of the opposite cabinets. The input device is a sheet steel cabinet attached to the end of the power transformer. Cabinets, depending on the PTS power supply scheme adopted by the Project, are supplied: 1) for tight connection; 2) for connection through a disconnector; 3) for connection via a fuse disconnector. In the presence of a disconnector, the ero drive is displayed on the side surface of the block. The bottom of the box has two holes for power input, designed for three-core cables with a cross section of up to 150 mm 2.
Go to other sections: